Welcome to use the ZEC-8600 wireless high pressure nuclear phase apparatus produced by wuhan zhongke xinyi power technology co., LTD
Check the host: press the "open/off key" to boot, the screen shows normal, the upper right corner shows the power。
Exception: if the instrument crashes when using, long press "on/off button" cannot be properly shut down, please open the instrument behind the battery cover, press "K_Reset" reset, instrument can be reset to normal state。
Method 1: use the configuration of the test line reference connected to 220 v mains, if emitter buzzer, two lights flashing, receiving host to show the waveform and frequency of the corresponding information, the transmitter is normal;
Note: it is strictly forbidden to use wire to replace the test line, otherwise the instrument will burn out。 (test line internal limited flow resistance)。
Method 2: the emitter hooked up to the corresponding voltage grade on live line inspection, if the launcher buzzer, two lights flashing, receiving host to show the waveform and frequency of the corresponding information, the transmitter is normal;
Method 3: using high pressure test equipment, simulation of high voltage line for inspection instruments, if the launcher buzzer, two lights flashing, receiving host to show the waveform and frequency of the corresponding information, the transmitter is normal.
Insulation rod inspection:
Stretch the telescopic insulated rod to the full length to carry out the regulation of the pressure test. The specific voltage withstand voltage may refer to appendix A.
Tip: 1) when the maximum voltage of the pressure test equipment is limited, the insulation rod can be stretched to the full length, and the corresponding compressive test shall be carried out in each section;
2) there is no built-in conductor at the front of the insulation rod, and it can be tested with withstand voltage。
1. During field test, operators should operate according to the safety distance standard of the power department.
2。 Standard configuration insulation rod 3 meters, corresponding voltage level is less than 220kV。 If the measuring line voltage is higher than 220KV, please use the insulated rod with length greater than 3 m。
Do not exceed the handle position of the insulated lever when the nuclear phase is operated.